# 50 Amp Wire Size - Calculate Proper Wire Gauge/Thickness

50 Amp is a very common current requirement we need proper wires for, especially at home, in the RVs, boats, cars, etc. While transferred power depends on the voltage applied to the circuit, energy efficiency and cable temperature depend on the wire thickness and its electrical resistance.

When calculating proper wire thickness and circuit breaker, there are a few important things to consider. But, whatever You do, safety first.

Published: April 1, 2022.

## AWG Wire Sizes Chart

The following comparison chart lists AWG wire sizes with the most important features of such wires, including the "Ampacity" - wire current carrying capacity.

 AWG# Diameter(mm/inches) Area(mm2/in2) Resistance (Copper)(mΩ/m;mΩ/ft) Ampacity (A) @60°C/140°F @75°C/167°F @90°C/194°F 4/0(0000) 11.68400.4600 107.21930.1662 0.16080.04901 195 230 260 3/0(000) 10.40490.4096 85.02880.1318 0.20280.06180 165 200 225 2/0(00) 9.26580.3648 67.43090.1045 0.25570.07793 145 175 195 AWG 0 (1/0) 8.25150.3249 53.47510.0829 0.32240.09827 125 150 170 1 7.34810.2893 42.40770.0657 0.40660.1239 110 130 145 2 6.54370.2576 33.63080.0521 0.51270.1563 95 115 130 3 5.82730.2294 26.67050.0413 0.64650.1970 85 100 115 AWG 4 5.18940.2043 21.15060.0328 0.81520.2485 70 85 95 5 4.62130.1819 16.77320.0260 1.0280.3133 - - - AWG 6 4.11540.1620 13.30180.0206 1.2960.3951 55 65 75 7 3.66490.1443 10.54880.0164 1.6340.4982 - - - AWG 8 3.26360.1285 8.36560.0130 2.0610.6282 40 50 55 9 2.90640.1144 6.63420.0103 2.5990.7921 - - - AWG 10 2.58820.1019 5.26120.0082 3.2770.9989 30 35 40 11 2.30480.0907 4.17230.0065 4.1321.260 - - - AWG 12 2.05250.0808 3.30880.0051 5.2111.588 20 25 30 13 1.82780.0720 2.62400.0041 6.5712.003 - - - AWG 14 1.62770.0641 2.08090.0032 8.2862.525 15 20 25 15 1.44950.0571 1.65020.0026 10.453.184 - - - 16 1.29080.0508 1.30870.0020 13.174.016 - - 18 17 1.14950.0453 1.03780.0016 16.615.064 - - - AWG 18 1.02370.0403 0.82300.0013 20.956.385 10 14 16 19 0.91160.0359 0.65270.0010 26.428.051 - - - 20 0.81180.0320 0.51760.0008 33.3110.15 5 11 - 21 0.72290.0285 0.41050.0006 42.0012.80 - - - 22 0.64380.0253 0.32550.0005 52.9616.14 3 7 - 23 0.57330.0226 0.25820.0004 66.7920.36 - - - 24 0.51060.0201 0.20470.0003 84.2225.67 2.1 3.5 - 25 0.45470.0179 0.16240.0003 106.232.37 - - - 26 0.40490.0159 0.12880.0002 133.940.81 1.3 2.2 - 27 0.36060.0142 0.10210.0002 168.951.47 - - - 28 0.32110.0126 0.08100.0001 212.964.90 0.83 1.4 - 29 0.28590.0113 0.06420.0001 268.581.84 - - - 30 0.25460.0100 0.05090.0001 338.6103.2 0.52 0.86 - 31 0.22680.0089 0.04040.0001 426.9130.1 - - - 32 0.20190.0080 0.03200.0000 538.3164.1 0.32 0.53 - 33 0.17980.0071 0.02540.0000 678.8206.9 - - - 34 0.16010.0063 0.02010.0000 856.0260.9 0.18 0.3 - 35 0.14260.0056 0.01600.0000 1079329.0 - - - 36 0.12700.0050 0.01270.0000 1361414.8 - - - 37 0.11310.0045 0.01000.0000 1716523.1 - - - 38 0.10070.0040 0.00800.0000 2164659.6 - - - 39 0.08970.0035 0.00630.0000 2729831.8 - - - 40 0.07990.0031 0.00500.0000 34411049 - - -

Note: Ampacities are given for enclosed wires @86°F (@30°C) ambient temperatures.

## Calculating the Right Wire Gauge

When looking for the right wire thickness for 50 Amps current, first we have to find the proper wire thickness at the required temperatures as listed in the chart.

Note: Wire thickness is very often calculated for temperatures of 167°F (75°C), but 140°F (60°C) is already a hot enough temperature to prevent an adult to hold the cable with an unprotected hand for more than a few seconds. Choosing a lower temperature adds an additional safety level.

Another important requirement for 50 Amps wire size is the "80% Rule":

For example, when calculating wire size for 50 Amps circuit, we will go for the wire that features Ampacity of:

Ampacity = 50 Amps / 0.80 = 62.5 Amps

So, for a 50 Amps wire, we will choose the wire with the Ampacity of AT LEAST 62.5 Amps and the required temperature.

If we check the wire chart, we will find that there is no wire with an Ampacity value of 62.5 Amps, so we will choose the next best thing:

T = @60°C/140°F) → Ampacity = 70 Amps → AWG 4

T = @75°C/167°F → Ampacity = 65 Amps → AWG 6

T = @90°C/194°F → Ampacity = 75 Amps → AWG 6

As one can see, different maximum temperatures also mean different wire sizes - some electricians may consider AWG 4 wire an overkill for a 50 Amps current, especially if the wires are not extra long, but better safe than sorry.

So, for short, we can safely say:

50 Amps wire size → AWG 4 wire

AWG 4 wire features:

- diameter: 0.2043 inches (5.189 mm),

- area: 0.0308 inches2 (41.7 kcmil, 21.1506 mm2),

- electric resistance: 0.2485 mΩ/ft (0.8152 mΩ/m),

- Ampacity: 70 Amps @60°C/140°F, 85 Amps @75°C/167°F and 95 Amps @90°C/194°F.

Choosing thicker wires, in this example, AWG 4 instead of AWG 6, decreases energy losses and the operating temperature of the wires.

But, just note that thicker cables also require more space, they are heavier, thicker, often more difficult to work with, etc.

Note: Never, but really never use thinner cables than required - for example, don't go for AWG 8 wires (or thinner) for 50 Amp circuits.

## 50 Amps Circuit Breaker

When looking for a proper circuit breaker, finding proper amperage if the circuit breaker is very simple - for a 50 Amps circuit, one needs 50 Amps electric breaker.

Unlike wires, which can be somewhat thicker, for a 50 Amps circuit, one should NEVER use a stronger circuit breaker. Also, weaker electric circuit breakers may trip too often, so, they are not recommended either.

Note: if You are unsure, contact a local certified electrician for more information, including local laws and regulations.

Long Story Short: When looking for a 50 Amp wire, go for AWG 4 copper wires, especially if the cable is longer than 30 feet (~9.2m) and shorter than 100 feet (~30m).

For shorter cables, AWG 6 wire may be used, but one risks somewhat higher operating temperatures.